Yes, the most common is to integrate three cores (2 for protections and 1 for measure), but you can do many more combinations. The limitation is in the internal space, so we must look for low output powers, high currents in primary and if possible use 1A secondary output. You can also use the CT integrated for monitoring and synchronization the breakers.
High Voltage Products
If you want to purchase a product, need any pricing information or need help or support from ABB, please contact your local partner.