Due to a leakage, the SF6 density in one gas compartment decreased quickly and I wonder, if I have to de-energize the GIS immediately or can still keep it on-line until I have an engineer on site to fix it.
No. All GIS gas compartments must have at least “minimum functional density”. If the density goes below minimum functional density the concerned gas compartment must be switched off immediately.
High Voltage Products
If you want to purchase a product, need any pricing information or need help or support from ABB, please contact your local partner.