The complexity of the monitoring system should relate to the importance of the individual asset. For breakers with high importance, a high precision of the assessment is desirable and as a result usually more parameters are monitored. For breakers with average importance, monitoring of some key parameters is usually sufficient (e.g. SF6 density, operating mechanism, breaker timing).
High Voltage Products
If you want to purchase a product, need any pricing information or need help or support from ABB, please contact your local partner.